Welcome to the new Xylem Flow Control Website
You have perhaps been redirected here from one of our Brand websites, this new site brings together all our brands under one combined site with the same features and content you had before and some new.Close this messageX
Mount the pump in a dry, ventilated location. The inlet strainer must be installed between the fresh water supply and the pump inlet port. The supply tank should be at least half full prior to initial operation.
NOTE: The VSD electronics require a battery installed in the DC power supply when using an AC to DC converter or battery charging system.
IMPORTANT: Polarity of electrical connections is very important. Insure that the RED () motor lead is connected to a fused positive DC circuit. The BLACK (-) motor lead must be connected to the negative DC circuit. In the event that polarity is reversed, in-line fuse must be replaced.To prime the plumbing system, open all the faucets and turn on the power to the pump. Shut off each faucet as it begins to run free of air. As the last faucet is closed the pump will slow down and shut off.